Oil Boiler Breakdown
Called out last night to an Oil Boiler Breakdown in Clonsilla, Dublin. Old Bentone Burner has a seized motor and couldn’t turn to pressurise oil pump or turn the fan for air flow.
This Oil burner was supplied with the Oil boiler when it was installed in 1997. Unfortunately it would be too costly to replace the motor. Instead we fitted a new Riello G3b Oil Burner which was suitable. With the change of the mounting plate, the new oil burner fitted perfectly and was installed in 45 minutes. We then balanced the burner by way of adjusting the fuel pressure and air shutter for optimum efficiency. A complete oil boiler service was then completed and the boiler was found to be in excellent condition throughout. When the boiler was reassembled we put on the Flue Gas Analyser and checked the efficiency, this 21 year old oil boiler was burning at 88.7% efficiency which is fantastic.
If you are having problems with your Oil Boiler or Condensing Oil Boiler we can help. We offer a 24hrs Emergency Oil Boiler Breakdown Service in Dublin and surrounding areas, just call 0874048238 or contact us for an appointment.
We Service Grant Oil Boilers, Firebird Oil boilers, Warmflow Oil boilers and all major manufacturer Oil Boiler types.
We Service Riello Oil Burners, Bentone Oil Burners and Nu-way Oil Burners.